Hotel Water Softener Size Calculator and Guide
Calculate the proper size and model for a hotel water softener. The following online, free calculator can be used as a guide for hotel water softener sizing. For general water softener sizing, see the industrial water softener sizing calculator instead.
Hotel Water Softener Sizing Guide
There are many variables in sizing industrial hotel water softeners beyond the scope below. Water pressure, temperature, flow rate and cubic feet of resin per tank also affect water softener sizing, so these guides are to be used for quick estimates only.
For detailed industrial water softener sizing including configurations, control types or pretreatment for reverse osmosis, deionization, etc., please email or call Nancrede Engineering at 888-569-2837. We are happy to help, and our experience will save you countless hours.
How much does it cost to operate a hotel water softener? See our industrial water softener operating cost calculator.
Nancrede Engineering also offers preventative maintenance, engineering consultation, equipment leasing, financing, and build, own, operate options. Let us know if you would like information on how these services can help you reduce downtime and capital risks.
* Peak Continuous GPM is not instantaneous peak flow rate. It represents a continuous high flow rate at peak times of the day (e.g. for 30 minutes or more).
** Instantaneous peak flow rate is the maximum GPM for a short time (e.g. 1-5 minute period).
Most failures in water softener sizing occur when softeners are sized too big as opposed to too small. The guide below shows the minimum continuous flow necessary to prevent water softener channeling.
Looking for parts? We carry parts for water softeners from Culligan, Marlo, Bruner, Lakeside and Siemans and more.
Learn more about: